Solar electrolytic table salt sodium hypochlorite disinfection equipment uses solar panels to provide power, prepare sodium hypochlorite on the spot and add it according to flow changes, so as to achieve the disinfection effect and achieve water supply.
亚游集团官方1) On-site preparation of sodium hypochlorite
亚游集团官方Manually prepare 100 liters of 2 ~ .3 percent dilute saline and add it to the storage tank. Turn on the power.
亚游集团官方The system will automatically enter the electrolysis state, and the dilute brine will produce sodium hypochlorite solution. The operation is about
亚游集团官方Every 15 to 30 days--times.
2) Accurately add disinfection
亚游集团官方The metering metering pump adds a certain amount of sodium hypochlorite to the lifting pipe according to the flow rate of water extracted from the well or ditch in real time detected by the flow meter and enters the reservoir. This operation is carried out automatically, when the water flow is large, the corresponding dosage is large, when the water flow is small, the corresponding dosage is small, and there is no accident of adding medicine when no water is supplied at night, causing an accident of excessive disinfectant.
3) One-click descaling
According to the on-site water quality and equipment operating conditions, descaling is performed regularly, and PLC control realizes one-key descaling to ensure the efficiency of electrolysis.
亚游集团官方4) Remote operation and maintenance
The equipment is equipped with a remote operation and maintenance module, which can collect and transmit parameter data such as the pump valve, liquid level, and temperature of the disinfection equipment. It supports the 4G wireless transmission function of the mobile phone card, and can remotely monitor the operation of the equipment through the network.
Features compared to type I
亚游集团官方1.Enlarge solar power generation panels to improve power generation efficiency and endurance;
2.PLC intelligent control, higher degree of automation;
3. Add remote operation and maintenance module to better realize remote operation and maintenance.